Stable Biogas Purification System , Biogas Scrubbing System 0.7 – 0.75 Kg / L
Detailed Product Description
|Coat Thickness:||0.25-0.45mm||Holiday Test:||Up To 1500V|
|Type:||Bolted Steel Tank||Material:||Glass-Fused-To-Steel|
biogas purification equipment
h2s removal system
Large scale biogas plant Chemical desulphurization system/ H2S purification
Why we need desulphurization
Removal of H2S is often required for reasons of health, safety, environment and corrosion of equipment such as gas engines, boilers and piping. Desulphurization is also is necessary when biogas is upgraded to natural gas quality and injected in the grid.
Iron Oxide Desulfurizer is made of iron,manganese salt and their oxide as raw material,pass through the process chemosynthesis to be active oxide,then add the assistant and binder to make it columnar solid .
It has features of larger sulfur capacity ,small resistance,high purification capacity and good water resistance .
2.Physical&Chemical Properties and Service conditions
|Saturation sulfur capacity||≥550mg/g||(under normal temperature, the original size)|
|Desulfurization precision||≤0.5ppm||Contact time or 30 seconds, the import H2S10-15 mg/Nm3, airspeed acuities 1000 h – 1, temperature 15 °C to 55|
|specific surface area||70~80m2/g|
|Radial pressure strength||≥40N/cm|
|Water resistance strength||With water or distilled water boiling 15 min above, not natural broken or mud change, flooding after drying constant regeneration activity|
|main ingredients||Fe2O3·xH2O Fe(OH)3·xH2O|
|APPLICATIONS||For the nature gas,coke oven gas, water gas , biogas|
3.Desulfuration and Renewal Principles of the ferric oxide
Desulfuration Reaction: Fe2O3.H2O+3H2S=Fe2S3.H2O+3H2ORenewal Reaction: 2Fe2S3.H2O+3O2=2Fe2O3.H2O+6S (strong exothermic reaction)